How long should you flush your eyes with water at the eye wash station?
Eyewash stations should be designed to deliver fluid to both eyes simultaneously at a volume of not less than 1.5 litres/minute (0.4 gallons/minute) for 15 minutes.
How do I turn off eyewash station?
Once an eyewash station has been activated it cannot be turned off. The eyewash solution will flow until the cartridges or reservoir have been emptied.
How often should eye wash stations be checked or activated?
According to ANSI/ISEA Z358. 1-2004, plumbed emergency eyewash and eye/face wash stations should be visually inspected and activated every week. Equipment requires annual servicing to ensure effective operation. Proper training covering the location and use of the eyewash is also vital during an emergency.
Does an eyewash station needs to be located no more than 10 seconds or less than 55 feet away from a work area?
However, some of the requirements include that eyewash stations be located no more than 10 seconds (or about 55 feet) from hazardous work areas. The station should be located on the same level as the hazard, have a clear path for travel, be installed in a well-lit area, and be marked with a visible safety sign.
How often should eyewash station water be changed?
every three to six months
As a general rule, eyewash stations filled only with potable water should be drained and refilled monthly. Stations with water and preservative should be changed every three to six months.
Do eyewash stations need drains?
Most eyewash, eye/face wash and safety station units are designed with waste connections for connection to drain piping. For emergency showers and for other units without waste connections, floor drains should be provided.
How far apart do eyewash stations need to be?
OSHA interprets the phrase “within the work area” to require that eye/face wash units and emergency deluge showers both be located within 10 feet of unimpeded travel distance from the corrosive material hazard or, in the alternative, within the distance recommended by a physician or appropriate official the employer …
How far apart should eyewash stations be?
Eyewash safety stations must be installed within 10 seconds or 55 feet from the hazard. The spray pattern must measure between 33”–53” from the floor the user will stand on (section 5.4. 4).
How do you change the water in a eyewash station?
How to Refill a Self-Contained Eyewash Station
- Drain all the water from the tank.
- If possible, remove the spray heads and any tubing so they can be cleaned.
- Clean the exterior of the unit, and then use a soft brush, mild soap and warm water to clean the inside.
- Drain the wash water and rinse thoroughly.
Can you use tap water for eye wash station?
The standard recommends that portable eyewash stations use a preserved, buffered pH-balanced saline solution instead of plain tap water because tap water can cause painful damage even to healthy eyes. Tap water is not buffered, nor does it contain any of the necessary salts.”
What are the OSHA requirements for eye wash stations?
assembled and installed in accordance with the manufacturer’s instructions
How to clean eyewash station?
– Locate floor drain and adjust accordingly. For example, we recommend using a plastic garbage bag to catch the water if your drain pipe does not extend to the floor drain – Protect nearby objects from possible over spraying water. – Wrapping an old rag around the two shields will help to prevent water from leaking onto the floor.
How to use an eyewash station?
– Is the water clear? – Are the jets working properly? – Is the area around the station clear of obstructions? – Is there a bucket located under the eyewash to collect runoff? – Are there any leaks?
What is emergency eye wash?
The path from the hazard to the safety shower shall be free of obstructions and tripping hazards.